Zibo Taylor Heat Exchange Equipment Co., Ltd. specializes in providing plate heat exchanger selection, heat exchanger unit maintenance, plate heat exchanger rubber pad accessories and other services. Analysis of the fouling reasons of plate heat exchangers : the gap between the flow channels is small (2.5-6mm), and the particle debris with a diameter greater than 1.5 ~ 3mm is easy to block the plate channel, causing the pressure drop of the equipment to deteriorate sharply, causing the equipment to change due to blockage. The thermal capacity is greatly reduced, which seriously causes the continuous production interruption of the device. Because of the large amount of impurities in the circulating water, similar devices E208 / E209 have been blocked for many times, resulting in frequent shutdowns of the devices, which has a certain impact on the economic benefits of the enterprise. Later, an easy-to-remove filter was added before E208 / E209 to ensure long-term operation of E208 / E209. Therefore, a coarse filter or a backwashing device can be provided at the inlet of the medium as required to effectively prevent the blockage of the plate heat exchanger.
For more information, please Baidu: Taylor Plate Heat Exchanger
Zibo Taylor Heat Exchange Equipment Co., Ltd. http://bigsaiwan.com welcomes you!